This light up and it is not an choice this time....I additionally want to say thanks to all of the wonderful folks who post and answer right here! That is my first query but i have learned so much from other posts and answers over the years!. There are currently 4 wires popping out of the ceiling container - / black and white to 1 lightbulb and a black and white to the alternative mild bulb. The new ceiling light (it is not a fan) has most effective a single black and a unmarried white. There is the green floor in the mild but no longer from my 1940's ceiling box which become ordinary for those homes, so i'm used to that. I am guessing the 2 units of wires are due to the fact the two switches - my question is - how do i nicely re-connect to have the light function and no longer danger a hearth or bodily harm?.