Honeywell 4 wire zone valve wiring diagram - My unpleasant tough comic strip above on thi spage desires to be re-drawn neatly, but there i show how we efficiently stressed out-up a mixed logo sector valve set up. I had two honeywell area valves and one white rogers region valve. [Click to enlarge any image]. To govern up to 8 heating zones you would possibly twine multiple preferred switching relays together as proven on this taco wiring diagram. This illustration is from the taco sr503-four switching relay guidance sheet whose hyperlink is given above. [Click to enlarge any image]. Wire sector valve diagram with primary pics to honeywell valves wiring striking wire region valve diagram with simple pix to honeywell valves wiring hanging wire zone valve diagram with primary photos to honeywell valves wiring striking.
When i got into that trouble years in the past i was wiring up a honeywell sector valve to a machine already using flair quarter valves. I referred to as my heating dealer who had dave ferris (now retired) on deck to reply wiring questions. On most u.S. Structures the circulator runs sending water thru the open zone loops and a primary control at the boiler, tracking water temperature, in reality turns the boiler on or off as needed to re-warmth the water. Further for your manage, the honeywell l6006c 1010, honeywell's l8124a,c and 8151a are triple aquastats similar in characteristic, regularly used to manipulate zone valves. Where you could run into problem is with an set up that has a combination of different brands of region valves. If so, the wiring instructions for one employer can be one of a kind from the opposite. Nicely stressed, the character thermostat calls for warmth, the zone valve opens, while the valve is fully open an cease switch within the valve connects a second pair of wires that activate the circulator pump again on the boiler.
We consist of wiring diagrams and installation commands for most zone valve model and multi-sector controllers, and we describe unique wiring issues that may occur if you blend different sorts, manufacturers, or fashions of heating zone valves at the identical hydronic heating (warm water heating) system. A few years back i transformed approximately 1/4-1/3 or my house into hydronic radiant floor warmth strolling off same quarter because the baseboard. The fellow who sweated the tubes and zoned it out has by no means come lower back to hook up the quarter controller.